- Click on BOS Components in the right toolbar then select the appropriate component for your system from the sub-menu.
- Combiner box
- Load center
- Service panel
- Click on the Connect icon, then starting from either string end, click to connect your string(s) to your inverter/combiner box.
- Think of connections like conduit runs on the roof/wall
- Continue to click on components to connect them together
For microinverter systems, the 'string' feature connects modules in parallel on a single trunk cable. Red indicates the trunk cable ampacity has been exceeded, where the trunk cable ampacity is defaulted to the standard 20 amps.